RWH is the technique of collecting, storing and distributing rainwater for multiple uses. The collected water can be stored for direct use or diverted for borewell/groundwater recharge. In simple terms it is a way to capture the rainwater when it rains, for later use.
You, me and everybody! It will not only provide you with water in times of acute water shortage, but will also recharge the groundwater and increase its level.
Rainwater is the ultimate source of all the fresh water that we use. In India, rainfall occurs in short periods of high intensity, allowing the rain falling on the surface to flow away fast. This leaves little scope for recharging the groundwater, which results in water scarcity in most parts of the country. Through RWH, this erratic rainfall can be conserved, stored & used as per convenience, either directly or for recharging groundwater.
RWH can be done in homes, apartments, societies, schools, institutions, commercial premises and any other space as long as there is a catchment area in the form of a roof or open space to capture the rain.
Domestic rainwater harvesting is a relatively simpler affair, where even a rain barrel can serve as a storage unit for rooftop RWH. Individual homes have successfully implemented this easy and eco-friendly method of augmenting household-level water availability. Farmers also have implemented RWH to transform a barren piece of land into a self sustainable, lush green farm.
No, existing buildings can also implement RWH by modifying the existing plumbing and making additions, if necessary.
The rainwater harvested depends upon the catchment area, the rainfall pattern in the area and the drainage/ collection system used.
To understand the potential for rainwater harvesting, lets take the example of a house in Delhi with a terrace area of 100 sqm. Taking the average annual rainfall in Delhi as 600 mm, and assuming 70% harvesting efficiency (as some rainwater will be lost due to evaporation, collection etc.), we can calculate the amount of water harvested thus:
Volume of water harvested = 100 x 0.6 x 0.7 = 42,000 litres
This volume is more than twice the annual drinking water requirement of a 5-member family, whose average daily drinking water requirement is 10 lpcd.
The cost will vary depending upon the catchment area and the conveyance/ storage structures finalised. RWH can be installed at a very low cost in large plots where public buildings, schools & colleges are located, and this cost is negligible to the total construction cost, if integrated with the building design.
If planned in an existing building, the cost is higher due to extra plumbing involved, but the returns are rich in terms of recurring benefits.
The rainwater that falls on the roof is pure, but since it comes in contact with various surfaces on its way to the storage units, some dust and leaves may get carried away with it. This can be reduced if the terrace is swept before the rains. However, even if some dust or leaves go into the sump, they do not cause any harm as long as the water is boiled before consumption.
Various filters can be utilised to remove such suspended pollutants from the rainwater collected to make it safer for consumption.
Rainwater harvesting can broadly be divided into 3 categories based on the types of usage, the area in which harvesting is carried out and the people involved.
The RWH system must ensure that not a drop of rainwater falling within the premises is let into the sewerage or wasted as runoff. This can be achieved only if the method adopted within the premises satisfies the following criteria:
Existing unused structures like dried open wells, sumps etc can be used for RWH as also defunct borewells, instead of constructing recharge structures. This will also reduce the total cost.
Source : India Water portal
Last Modified : 2/13/2020
This topic provides information about Zero tillage...
This topic covers information related to Acute res...
This topic provides about *99# Service- Innovative...
This topic provides information related to steps t...